No.12, Haotian Street, Liangxiang, Fangshan District, Beijing-102401, China
Product Introduction Rated current: 1A~2000A Stud or terminal block optional ( ≥250A it is copper bar) Could be customized according to the actual interference situation of customer’s working field Features and Benefits -- Prevention of the electromagnetic interference of inverter towards...Chat Now
Rated current: 1A~2000A
Stud or terminal block optional ( ≥250A it is copper bar)
Could be customized according to the actual interference situation of customer’s working field
Features and Benefits
-- Prevention of the electromagnetic interference of inverter towards controller and solar panel.
-- Prevention of the electromagnetic interference of inverter towards other grid-tied equipments.
-- Effectively get rid of the electromagnetic pollution of inverter output current, guarantee the grid power quality.
-- Effectively eliminate the negative influence of radiated interference of solar panel towards inverter and controller.
-- Greatly improve system reliability and effectiveness.
-- 600VDC, 1200VDC or above high voltage versions available upon request.
-- Strict temperature rise control and much better performance than actually required assure product reliability even under special working conditions.
PV inverters, high power frequency conversion device, other electronic equipment comprising inverters
Important Notes on EMI Filter Application:
Ⅰ. Storage of EMI Filters:
EMI filters mustn’t be left out in the heat of the sun or exposed to the rain, it should be stored in warehouse with good ventilation, surrounding temperature between -30℃ and +65℃ and the highest relative air humidity lower than 90%, and there is no corrosive liquid or gas.
Ⅱ. Installation of EMI Filters:
■ EMI filters should be installed at power input, and the line inside the chassis be as short as possible to reduce radiated interference.
■ Both input and output lines of EMI filters neither be intersected nor be tied up by string.
■ Make sure the mounting flange fully grounded, and keep the ground cable as short as possible if filters are connected to other equipment.
■ If the terminal is stud, please use two spanners to fasten the screw nut when connecting to avoid stud rotating and thus causing changes to the internal circuit and consequently leading to filters arcing, short circuit, broken down or the filtering effect worsened. First use spanner1 to fix the screw nut near the metal case, then use spanner2 to tighten the screw nut in front( shown as Figure1), otherwise the terminals may be damaged. Apply the same for the connection of other phases.
■ Keep the tools fastening the stud be vertical to the metal case of filter when installing terminal block filters( shown as Figure2), must not tilt( shown as Figure3), otherwise the terminal blocks may be damaged.
Ⅲ. Reminding and Warning：
Please read all the safety warnings and instructions before mounting filters and putting them into use:
■ Don't take terminals as supporting point when moving filters to avoid the terminals distortion, loosening or broken.
■ The protective earth connections shall be the first to be made when the EMC filter is installed and the last to be disconnected.
■ Filters generate leakage current, please make sure they are well grounded before put into operation.
■ If the rated current is higher than 50A, we recommend grounding by the earth terminals but not only through the metal case of filters.
■ Danger of electric shock: EMC filters contain components that store an electric charge. Dangerous voltages can continue to exist at the filter terminals for longer than five minutes even after the power has been switched off.
■ The working conditions of EMI filter should comply with the technical parameters stated on the label, over voltage or overload could cause damage to filters. It is suggested to take proper over current protection measures.
■ Current drop occurs when the surrounding temperature rise, fail to follow the current drop requirement may lead to impermissible exceeding of the component temperature, as a result the service life of filters will be shortened after long time running.